Q: We are considering ordering the Moore Industries SPA/0-100mV/2 PRG/U/-SOL [DIN]. Can we power it using 24VDC? If so, what is the power consumption and how do we terminate? Also, can you please confirm whether this unit is Class 1 Div2, group A,B,C,D?
A: The SPA can be powered with 24VDC. It accepts any source voltage in the ranges of 22-300Vdc or 90-260Vac. Power Consumption is 2-4W, nominal; 6W, maximum.
If you specify the -HS option (hermetically sealed relays) then it is approved for Class 1 Division 2 locations when installed in an enclosure that provides sufficient mechanical and environmental protection. Usually, a NEMA 4 rated box will serve. See page 1 of the data sheet (click the link to open the download page).
The sample model number with -HS option and with a NEMA 4 enclosure is:
The –SOL option in this model number indicates a specially engineered SPA used to monitor the health of solenoid valve coils.
Do you want more information? Download the data sheet. Or visit the catalog.
Need to get price or availability or have a technical question?
Send us a message using E-Help.